The VFB Plus Ventilated Fire Barrier is a ‘Open State’ Cavity Fire Barrier system for ventilated cavities of up to 500mm which employs a high expansion intumescent seal fixed to TENMAT High Density Mineral Wool. The product has undergone extensive fire testing and is suitable for use within the majority of construction types, enabling the versatile system to be specified with confidence and provide the installer with a simple, time saving and site friendly solution.
The VFB Plus Ventilated Fire Barrier consists of a high expansion intumescent strip fixed to TENMAT High Density Mineral Wool and encased in polythene. The VFB Plus can be mechanically fixed both horizontally and vertically within ventilated cavities behind rainscreen or cladding systems to act as a cavity fire barrier.
The VFB Plus is a particularly versatile Ventilated Fire Barrier which can be installed in a wide range of construction types. The product is simply mechanically fixed in position to leave up to maximum 44-54mm* air gaps.
- Tested for up to 2 hours
- Continuous Free Air Space from 50mm up to 500mm
- Quick & Easy Installation
- Satisfies Building Regulations
- Fire & Age Tested
Fire Testing Approvals
Up to 2 hour fire tested to standards including: BS476: Parts 20 and 22, EN1363-1: 1999, EOTA TR31 and assessed to TGD19 ‘open state cavity barriers’ to ASFP standards for ventilated facades.
Tested in combustible and non-combustible cavity constructions.
Test No.’s: Chilt / A10030
Chilt / IF04065, Chilt / IF06005
Chilt / IF06013, Chilt / IF06040
Chilt / IF08038, Chilt / IF08052
Chilt / IF09011, Chilt / IF09032
Chilt / IF09093, Chilt / A06037
To suit from 50mm up to 500mm cavities
HELP – DOWNLOADING FILES
Please note that some web browsers may open Revit files in a new tab instead of downloading them. You can change this behaviour in your browser preference settings or by following these steps.
1. Right click on the download button or link.
2. Choose “save link as”.
BIM FILE DISCLAIMER
Although the integrity of these files is checked on creation, TENMAT accept no responsibility for any loss or damage, whether direct or consequential, caused by files which may turn out to be corrupt. Consequently it is the sole responsibility of the person downloading the file to ensure they have the appropriate IT protection measures in place.