UP TO 4 HOURS FIRE RESISTANCE WITH TENMAT FIREFLY FF109
TENMAT’s FIREFLY 109 CE Marked Pipe Fire Sleeves typically provide 2 Hours’, and in certain applications up to 4 Hours’ Fire Resistance* to various plastic and metal pipes.
The Fire Sleeves have been fire tested to EN 1366-3:2009 & BS 476. The European Technical Approval (ETA-12/0332) and EC Certificate 1224-CPR-0341 enables the range to be CE Marked and used throughout the EU. The EN fire testing included pipes tested with Uncapped/Uncapped (U/U) pipe end configuration as required for ventilated systems. (FF109+ version only)
The FIREFLY 109 Pipe Fire Sleeves are particularly suitable for use in plasterboard partitions, but can be used in blockwork walls and floors.
EXAMPLES OF APPROVED APPLICATIONS
Independently Third Party Assessed:
30 Minute Partitions
- Single Board from 72mm upwards
60 Minute Partitions
- Single & Double Board Systems
- Single Layer Ablative Coated Fire Batt
120 Minute Partitions
- Double Board Systems
- Double Layer Ablative Coated Fire Batt
CE Mark Approved:
- 3rd Party Assessed and Audited
BS 476 and BS EN 1366-3 Fire Tested
- Including Uncapped/Uncapped testing
(only FF109+ version tested U/U)
Fire Tested & Assessed for Blockwork
- Up to 4 Hour Tested
To enquire or get more information on the full range of Tenmat Passive Fire Protection products contact us.